apc Back-ups cs 500 amber on battery light flashing
i just bought a ups and it is flashing the on battery light rapedly. it does this even with a battery removed. any ideas?
Это хороший вопрос?
Check your AC outlet! You have a mis-wired outlet.
“Check site wiring fault indicator (rear panel-top)
A lit indicator means that a shock hazard exists due to faulty building wiring , that should be corrected by a qualified electrician.
If the building wiring fault indicator is lit, one of the following conditions exist:
• Open or high resistance ground• Hot and neutral polarity reversal• Overloaded neutral circuit
Note: Improper building wiring will not prevent the UPS from operating but will limit it's protection capability. Faulty building wiring could result in equipmentdamagethatisnotcoveredbyAPC. Please refer to APC's Equipment Protection Policy for details.”
Был ли этот ответ полезен?
За последние 24часов: 2
За последние 7 дней: 5
За последние 30 дней: 22
За всё время: 956